Emergency lighting open door lock and alarm device should be set in the cold storeroom
Assembly technology of refrigerating unit in Guizhou refrigeration equipment installation
The storage, transportation and management of the goods in the warehouse shall be convenient for the warehouse to be reasonably divided and set up in the warehouse.
The storeroom should have emergency lighting, open door lock and alarm device, which can be saved by self or alarm.
The shelves in the storeroom should have enough strength and rigidity.
The refrigerator door around through the fence and fortification, with eye-catching logo.
The assembly type cold storage should have a balance window.
Oxygen respirators, gas masks, protective clothing, rubber gloves, wooden stoppers, pipe clamps, acidic drinks and other necessary protective appliances and rescue drugs should be equipped in the computer room, and located in the location that is easy to get. It is managed by the special person and checked regularly to ensure the use. The personnel concerned should master the use of oxygen respirator and other equipment and the method of rescuing personnel.
For the refrigerating machine room with high voltage control cabinet and distribution cabinet, special tools and protective equipment for high voltage electric operation should be configured.
There are two kinds of production methods for cold storage doors: one is to spray polyurethane foam into a pre made frame, and the other is to use insulation board.
When making cold storage doors, the polyurethane heat insulation board is generally used, because it not only has great strength, but also has good heat insulation effect.
The common cold storage door type: manual sliding door, sliding door, vertical lifting door, door hinge, door, door free return; generally speaking, some other special places the door should be used in heat preservation places is also included in the refrigerator door, such as gas valve, slaughtering workshop dedicated door etc..
The installation of Guizhou refrigeration equipment is considered to be divided into import and domestic doors according to the different origin, and the main entrance of the imported cold storage is Danish dan-doors cold storage door.
1, semi closed or full closed compressor oil separator should be installed, and the amount of oil in the oil business and live, the evaporation temperature below -15 degrees, should install the gas-liquid separator and add the amount of refrigerant oil.
2, the base of the compressor should be fitted with a damping rubber seat.
3, the installation of the unit should have room for maintenance, so that it is convenient to observe the adjustment of the instrument and valve.
4. The high pressure meter should be installed at the three place of the liquid storage valve.
5. The whole layout of the unit is reasonable and the color is consistent. The installation structure of each type of unit should be consistent.
The transport tools used in cold storage design and installation should meet the requirements of relevant standards.